Image Coming Soon
DO Supply, Inc. sells surplus and refurbished products which are sourced through independent channels. All warranties and support, if applicable, are with DO Supply, Inc. and not the manufacturer. DO Supply, Inc. is not an authorized distributor or representative for the listed manufacturers and makes no representations as to any quality control performed by any listed manufacturer on the products. Read more
DO Supply, Inc. sells surplus and refurbished products which are sourced through independent channels. All warranties and support, if applicable, are with DO Supply, Inc. and not the manufacturer. DO Supply, Inc. is not an authorized distributor or representative for the listed manufacturers and makes no representations as to any quality control performed by any listed manufacturer on the products.
Some of the products sold by DO Supply, Inc. may come with firmware installed on them. DO Supply, Inc. makes no representation as to your ability or right to download, obtain, or use any firmware provided by the product's manufacturer. To the extent you wish to use such firmware, it is your responsibility to comply with the terms of any applicable license or other such agreement related to the download, installation, or use of the firmware. DO Supply, Inc. makes no representation that the version of the firmware that is installed on any product it sells is appropriate for your needs or use. Further, DO Supply, Inc. does not sell, re-sell, or license software that may be needed to operate certain hardware and customers must obtain any necessary software licensing, maintenance, or upgrades from the manufacturer or other authorized source. To the extent any of the products sold by DO Supply, Inc. requires software for operation, you acknowledge that DO Supply, Inc. does not sell or license such software and that it is solely your responsibility to obtain the software or a proper license to use it from authorized sources. Read less
|Product Line||Series C M Frame|
The Eaton HMDL3500 Molded Case Circuit Breaker operates with 3 Poles and 500 Amps. It also has a F Frame and a Thermal Magnetic Unit Type.
We offer international delivery through FedEx, UPS, and DHL.
We are proud to offer a one-year DO Supply Warranty with all purchases.
We are happy to accept payment through all major credit card providers.
|Dimensions (W x H x D)||8.25 x 16 x 4.06 inches|
|Interrupting Capacity||100 kAIC at 240 Volts AC|
|Part Number/Catalog No.||HMDL3500|
|Product Type||Molded Case Circuit Breaker|
|Unit Type||Thermal Magnetic|
The Cutler-Hammer HMDL3500 is a high-interrupting circuit breaker that is also a thermal-magnetic breaker that is used to detect abnormal currents. This breaker combines the current detection techniques of an electromagnet and a bimetal strip that responds to temperature changes. This breaker is mainly used in distribution boards, and it has been designed by Cutler-Hammer and included in its C Series of molded case circuit breakers. The Cutler-Hammer HMDL3500 high-interrupting circuit breaker provides an amperage rating of 500 Amps and an operating voltage of up to 600 Volts AC. It also features 3 poles and it has been included in the M frame product line of Series C of the Cutler-Hammer circuit breakers.
Prior to the installation of the Cutler-Hammer HMDL3500 high-interrupting circuit breaker, it is recommended to mount the breaker in a vertical plane to allow maximum airflow. This breaker has been calibrated for an ambient temperature of 40 degrees Celsius, and if the operating temperature is higher than this, the breaker should be calibrated again or derated. If the breaker is going to be installed in an enclosure, users need to make sure that it provides a good means of ventilation. The performance of the Cutler-Hammer HMDL3500 high-interrupting circuit breaker is 65 symmetrical Amps at a voltage of 480 Volts AC. The Cutler-Hammer HMDL3500 high-interrupting circuit breaker should be used in system voltages within their ratings and in order to ensure a correct application and provide a good protection level, the interrupting rating of the breaker must be equal or it must overpass the amount of fault currents delivered in that exact point of the system.
Manufacturer Part Numbers (MPNs) are often difficult to read. Here are some commonly mistaken versions for the HMDL3500: